Just bought a 98 5th wheel with ducted Dometic AC &amp; ducted floor heat but no TStat but a telephone like cable hanging out the wall-do you have tstat?
1391147
This one will NOT work. If you have the phone plug it had a comfort control center CCC. You are going to need to get the Model and Serial number of the from AC( not the number off of the lower shroud). If you get that number and want me to look it up I will. 336-499-7662
2099725
Sorry, I have not had this issue. I do know that there is a damper/door between tge heat and cool systems that could affect didcharge air temp. There sre websites for envoy trailblazer that can help witg troubleshooting
503233
Oliver, mine also came with the relay output terminals. I have temperature sensors and a "normally open" attached to my oil furnace burner motor that senses a lockout state. Looks to be working well. Plan to attach the output relay to a phone dialer in the future.Jeff
1285624
I received everything shown in the picture, although I believe mine had the connector with the wires and sockets already assembled...I recommend soldering the wires to the factory harness, unless you have some good waterproof compression connectors. Twisting and taping, or even wire nutting throws off the temp reading by a couple degrees...Soldering fixed it, and mine now reads the correct temp...Been working for about 6 months.
1279360
Yes, I installed mine in my 5th wheel when the relay in the ceilin unit failed. Much cheaper than replacing the controller board in the ceiling A/C central unit which operated the ducted propane heater. Be sure you know how to hook it up.Be advised this thermostat does not have an on/off switch, so I place a small piece of paper or cardboard between the contacts when not in use. That way if the RV is just sitting in your driveway the heater can't run if the temp drops overnight.
1936365
Yes If you call me I will sell you this one for 75.00 + frt I had to replace my trans with a rebuild and it will void the 3yr 100,000 mile warranty if I remove jaspers pan 812.446.0211
79411
Manual transmissions don't have a pump. So the cooler hooked up isn't doing anything. Not even sure where you would hook up lines to the T5 transmission that came in that car. Probably doing more harm than good.
2246385
Yes it does. I've had mine installed for about 9 months now and it has worked flawlessly. Installation and setting up the wifi was a snap. As for another answer saying the temp sensor is erratic....I've not had that experience with mine at all. You can program the temp differential (how far the actual temp can vary from the set temp before the stat responds) so maybe that user has it set to too broad a range, I don't know or maybe just a faulty stat. Mine is set at a 2 degree range and works great. I use it on a Geothermal Heat/AC/DHW System and it actually handles the heat pump better than the stat that came with the unit. Yes it does. I've had mine installed for about 9 months now and it has worked flawlessly. Installation and setting up the wifi was a snap. As for another answer saying the temp sensor is erratic....I've not had that experience with mine at all. You can program the temp differential (how far the actual temp can vary from the set temp before the stat responds) so maybe that user has it set to too broad a range, I don't know or maybe just a faulty stat. Mine is set at a 2 degree range and works great. I use it on a Geothermal Heat/AC/DHW System and it actually handles the heat pump better than... » Read More Yes it does. I've had mine installed for about 9 months now and it has worked flawlessly. Installation and setting up the wifi was a snap. As for another answer saying the temp sensor is erratic....I've not had that experience with mine at all. You can program the temp differential (how far the actual temp can vary from the set temp before the stat responds) so maybe that user has it set to too broad a range, I don't know or maybe just a faulty stat. Mine is set at a 2 degree range and works great. I use it on a Geothermal Heat/AC/DHW System and it actually handles the heat pump better than the stat that came with the unit. « Show Less
1037512
Sorry to hear that they screwed up your order. Lets hope everything will be ok. They are good A/C's. I had purchased 2 12,000 units for rest of the house since they are 110/120 and not 240. The units were originally Air Temp made by Chrysler. I was trying to locate Air Temp but it kept coming up SPT. I guess they merged companies.
1726405
honestly, I didn't pay a whole lot of attention. I know it was identical to the radiator I pulled out as far as dimensions go. just know that the pt is a big pain in the ass for bleeding out the cooling system!!! I drove it around for a week and had no problems then hit the interstate drove 130 miles and it overheated!!! so keep that in mind if u have over heating problems!!!
728630
I own a 1995 F 350 Powerstroke that's has a 4R100 tranny.I have the Derale 14208 on my truck works great. You might look at a temp Gauge to go with it youll be surprised how much the temps drops.
411736
Mine went bad after 1 year. Maybe install, maybe product. Tear up whole floor? So we have no heat in floor. Dave
2098312
Same here I have a 99 had to splice the wires but works great. Well did fixed it a month ago and daughter rolled it last Friday. O boy do I miss it
244437
My brown dome unit came complete. I replaced the same type that lasted 28 years. I just pulled the old one and placed the new one, reconnected the electric, set the thermostat and waited for a warm day to fine tune the thermostat setting. Not all that noisy and it helps keep the attic temperature down.
604082
No, just received my pair in a box with the wiring. Had the lame air pillows in the box, but plenty of room to move around. The sensors are just in little plastic bags. I was changing them as a preventive maintenance, because my 5.3 Intake Manifold gaskets failed. Does anyone know if they can be tested before installing them? I'm paying a mechanic to do the work. Really don't want pay for the job twice, because Amazon does not know how to ship fragile items.
1855221
I used mine to interface to a zone controller so that would not be available as an option. I did not see any options on the programming of the stat. to control speed any way. My best guess from not seeing that option is that the thermostat would not control the speed but cant say for sure, I am not sure if your air handler has any sensors in it to detect if it needs to change fan speeds without a signal to do so from the thermostat, you could check on what actually controls the speed of the fan your equipment. This thermostat has tons of programming options and is the very best I have ever had or seen, but again I did not see programming options for speed control. I used mine to interface to a zone controller so that would not be available as an option. I did not see any options on the programming of the stat. to control speed any way. My best guess from not seeing that option is that the thermostat would not control the speed but cant say for sure, I am not sure if your air handler has any sensors in it to detect if it needs to change fan speeds without a signal to do so from the thermostat, you could check on what actually controls the speed of the fan your equipment. This thermostat has tons of programming options and is the very best I have ever... » Read More I used mine to interface to a zone controller so that would not be available as an option. I did not see any options on the programming of the stat. to control speed any way. My best guess from not seeing that option is that the thermostat would not control the speed but cant say for sure, I am not sure if your air handler has any sensors in it to detect if it needs to change fan speeds without a signal to do so from the thermostat, you could check on what actually controls the speed of the fan your equipment. This thermostat has tons of programming options and is the very best I have ever had or seen, but again I did not see programming options for speed control. « Show Less
1635714
No!!! We are currently suffering through ownership of a red top goespring...the repair guy replaced the whole heat pump system on Thursday...have only heard the heat pump come on once since then, now it is throwing new error codes.